Have you ever been on a Ductile iron pipe (DI pipe) installation with restrained joint gaskets and needed to uninstall a previously assembled joint? This is normally prompted by the need to replace a displaced or a “pinched” gasket. Proper gasket placement and attention during assembly is the best way to avoid such conditions, as detailed in a previous blog by McWane Ductile. Unfortunately, the problem often does not arise until the pipeline is hydrostatically tested. In today’s Iron Strong Blog, we will examine the “Dos & Don'ts" of uninstalling with DI pipe restrained joint gaskets.
Good Question! Today's Iron Strong Blog answers it. At first glance, you might think longer lengths mean fewer joints, and that has got to be better. So why don't all manufacturers make longer pipe? This perceived advantage is really a myth and we will look at that in a minute. In fact, there are more Ductile iron pipe plants in North America that manufacture 18-foot length pipe either entirely or as a significant portion of their product mix.
One question we often receive in the field is, "Can you use Ductile iron pipe (DI pipe) when running hot water or steam through pipe?" The answer to that question is YES, but there are several factors you must consider. For this Iron Strong Blog, we are going to look at these factors to help determine what products are needed for each application.
In a continuous effort to make your job easier, we are constructing an online submittal builder to quickly and neatly package your personalized presentation. Stay tuned!
Looking for answers to your DI pipe questions? Find decades of Ductile iron expertise with installation guides, videos, tip sheets, training resources, and more in our Learning Center.
GIVE ME ANSWERS
Stop struggling with those hard-to-figure field calculations and put ease and efficiency right at your fingertips with our Pocket Engineer for mobile and desktop devices.
McWane Ductile is proud to be a part of the McWane family of companies.